Schlage 468 Z-Wave Lock Integration With Leviton VRC0P Serial Interface
In this example we will review the steps needed to perform a manual reverse association with a Schlage 468 lock to a Leviton VRC0P Serial Interface. The reverse association is required for two-way communication between the lock and Serial Interface. This means if the lock changes state manually (locking or unlocking) this will be reported to the Serial Interface.
1. Include Devices
-Include lock and all other devices tobe part of the network, including the VRC0P last.
-Set associations to all other devices except 468 locks.
-This will typically be two-way communicating devices such as Vizia RF lights and thermostats.
Right click on the Serial Interface and select “RS232 Setup.”
-Select the devices to associate EXCEPT the 468 lock(s) and click ”Set Association. “
Open Diagnostics and select Routing Slave Associations
Select Routing Slave
-You will need to be near the lock you are associating.
Associate the Serial Interface
-Under “Non-Associated Device(s)” click on the serial interface to highlight.
-Once the Serial Interface appears in the “Associated Devices” column the action is completed
- To associate additional locks, select the next routing slave to be associated with the serial interface.
You should now be able to control your locks as well as see the status of it.
If you have any questions or issues, please give us a call at 800-282-8864 or email email@example.com
This article was created by Joel DeYoung - Technical Sales
|Posted by: Worthington Technical - Thu, Mar 9, 2017 at 8:47 AM. This article has been viewed 9783 times.|
|Online URL: http://worthingtondistribution.com/kb/article.php?id=36|
Powered by PHPKB (Knowledge Base Software)